Lawita Hotel install SGE Heat Pump for reduce CO2 and energy cost at Pattaya.
This project not over 90 guest room which if use electric heater must limit 4500 W per units x 90 room equal
405kW per hour but use SGE Heat Pump only 6kW x 2 equel 12kW per hour so we are design 12hour is 144kW only which
save much save as 261kW per day or equal 260kW x 3.9 baht per unit x 30 day equal 30,420 Baht per month and 365,040 Baht
per year and pay back period is 2.7 year .
This Project use cold air flow to lift controller room. with 10 ton
Movement SGE Heat Pump to site .
Lift SGE Heat Pump to top of building with 2 units model 25.
Pressure storage tank 6000 Liter and PPR PN20 of Thai PPR hot water line.
VDO show detail installation SGE Heat Pump ” Leafs ” Thai brand.
Training Course I the base control and adjust SGE Heat Pump model 25
Close up to open Lawita Hotel Energy Saving Project .
SGE team setting and commissioning heat pump .
Adpprove and testing detail SGE Heat Pump
This project SGE design cool air out at top of model
This specification use electricity only 5.8 kW hour with 12A. with 380V/50Hz
Thanks for the owner Khun Chang and engineer consultant team for prove and
request design for SGE Heat Pump team .